MAGNUM® Underfloor Heating Cable 152.9 m
Warning: Last items in stock!
This product is not sold individually. You must select at least 1 quantity for this product.
The MAGNUM Electric Heating Cable 152.9 m has been specially designed for installing in cement floors. The spacing between the cables determines the capacity per m2. This gives you the freedom to apply more capacity (faster reaction time, higher temperatures) or indeed lower capacity (constant or low temperatures) when installing. Installation is very simple because the cable can be shaped. It can be secured to the MAGNUM Isorol using aluminium tape and with dove-tail platesor tie-wraps onto the concrete net. Moreover, handy spacer strips are available for fitting directly onto the floor. The advanced thermostat takes account of the required warming up period, so that your floor is always at the right temperature whenyou want it. The lack of radiators on the walls provides optimal freedom for interior decoration and placing furniture.
Main heating element. Installed below the floor covering to convert electring current into warm. Can be adjusted to fit awkward spaces.
7 mm diameter
Control device. One can manage up to 23 m² / 16 amps. At least one should be included to every order.
+5 to +40°C
Fitting instructions with control check useful to measure voltage during installation.
for fitting and using
|Heating Power||2600 Watt|
|Cable diameter||7 mm|
|Wire||Chrome / Nickel resistance wire|
|Encasement||Aluminium earthed sheath|
|Spacers requried||10 mm|
At least one Thermostat should be added to every cable order, however if you want to order multiple cables to achieve length which is not listed on our website (example 80 m = 40m + 40 m) only one cable should be added with included thermostate, the other one should not include it. One thermostat can handle up to 23 m² / 16 amps.
Other available cable lengths are available below:
|Product||Length||Coverage||Spacing||Spacers required||Price (tax included)|
|MAGNUM Cable 300 Watt||17.60 m||1.80 m²||100 mm||10 m||£ 103.20|
|MAGNUM Cable 500 Watt||29.40 m||3 m²||100 mm||10 m||£ 126.00|
|MAGNUM Cable 700 Watt||41.20 m||4 m²||100 mm||10 m||£ 158.40|
|MAGNUM Cable 1000 Watt||58.80 m||6 m²||100 mm||15 m||£ 198.00|
|MAGNUM Cable 1250 Watt||73.50 m||7 m²||100 mm||25 m||£ 225.00|
|MAGNUM Cable 1700 Watt||100 m||10 m²||100 mm||25 m||£ 277.20|
|MAGNUM Cable 2100 Watt||123.50 m||12 m²||100 mm||25 m||£ 336.60|
|MAGNUM Cable 2600 Watt||152.90 m||14 m²||100 mm||35 m||£ 389.40|
|MAGNUM Cable 2900 Watt||170.60 m||16 m²||100 mm||40 m||£ 448.80|
|MAGNUM Cable 3300 Watt||194.10 m||18 m²||100 mm||45 m||£ 478.80|
This stylish, colourful and refined digital clock thermostat has been specially designed for electric heating systems. The MAGNUM X-treme Control is supplied with every MAGNUM floor heating set (Mat,Cable and Foil types), including external floor sensor, a built-in air sensor and three different frames that suit most brands of switching equipment. The MAGNUM X-treme Control is simple and intuitive to operate using touch sensitive buttons under the display. The new chameleon function is simple to adapt to the colour of your interior. The stylish screensaver shows the time, temperature and current mode without touching the thermostat. The MAGNUM X-treme Control has a new help function that appears after 10 seconds in the menu with a complete description of the setting in question. The MAGNUM X-treme Control also has a wooden floor function whereby the temperature is limited to 28°C. This makes the MAGNUM X-treme Control the idea and safe solution for every electric heating system.
In some situations the digital regulation is not required and so the preference is for a simple on/off operation. Specifically industrial applications where the heating must remain on at all times. Therefore MAGNUM has designed the Standard Control: a simple on/off thermostat with temperature regulation that is clearly easy to operate.
Parts necessary for installation, listed below are always included excepting thermostat which is optional to allow ordering Foil in custom sizes, like 20 m² = 10 m² + 10 m². In such case, one product should be added with chosen thermostat and the other with it not included. Spacer strips also being optional, help with the positioning and installation process. Cable can be fixed to the floow multiple ways, for example with tape, however spacer strips make it a lot easier.
This MAGNUM Heating product is manufactured from high quality, durable materials. To guarantee that your product functions optimally there are a few points of attention which are described in the Installation Instructions. We can only offer you the full guarantee if the system is correctly installed in accordance with these Installation Instructions. Carefully read the instructions prior to installation, do not forget the yellow centre page when doing so, and ensure that you have the correct tools and materials. The electrical installation must be carried out by a qualified electrician in accordance with IEE Regulations.Please visit www.magnumheating.com to find your local supplier if you have any questions, require more information or support.
Check the contents of the box before starting. A complete set consists of:
|MAGNUM Cable 300 Watt||17.60 m||1.3||177|
|MAGNUM Cable 500 Watt||29.40 m||2.1||109|
|MAGNUM Cable 700 Watt||41.20 m||3||76|
|MAGNUM Cable 1000 Watt||58.80 m||4.30||53|
|MAGNUM Cable 1250 Watt||73.50 m||5.40||42|
|MAGNUM Cable 1700 Watt||100 m||7.40||31|
|MAGNUM Cable 2100 Watt||123.50 m||9.10||25|
|MAGNUM Cable 2600 Watt||152.90 m||11.30||20|
|MAGNUM Cable 2900 Watt||180.60 m||12.80||18|
|MAGNUM Cable 3300 Watt||194.10 m||14.30||16|
The MAGNUM Cable is insulated and watertight and can be installed on Foil finished insulation (Kingspan or Celotex) or existing concrete bases. The construction of the cable also allows installation in wet spaces. The heating cable may never be installed under fixed objects like wall units, kitchen units, baths, or showers and must be able to give off its warmth unimpeded. The power supply must be disconnected during installation. All installations must be wired through a suitably rated MCB or RCCD when applicable. All installations in wet areas must be wired through a dedicated RCCD in line with the thermostat. All connections must be made by an approved Electrician in accordance with current IEE regulations. The electrical heating cable is patented worldwide and fully conforms to the European IEC 800 standards. The connector cable can be extended or shortened, there must always be at least 0.5 meter of connecting wire left. The heating cable cannot be shortened! The end seal cannot be broken. If multiple cables are installed in a space, they must be wired in parallel and a suitably rated junction box may be incorporated so that only one power cable runs to the thermostat. Maximum capacity of the thermostat is 16 Amperes. If fitting more than one cable set and the combined area length exceeds194 meters (3400 watts), a suitably rated Contactor will have to be fitted. The thermostat may only be installed by a qualified electrician. Before installing the MAGNUM Cable, the resistance reading should be taken and noted down on the inspection card in the center of this manual. Keep this inspection card in the meter cupboard in a visible place this is part of your guarantee! (see point 8) The sensor must always remain IN the sensor conduit. Fit cap to end of the sensor conduit. If the sensor ever needs to be replaced it can then easily be removed. The MAGNUM Cable can be used under various floor finishes - Tile, Marble, Slate, Wood, Laminate, Vinyl and Carpet. (Tog rate of carpet and underlay should not exceed 2.5). If using underneath a wooden floor or carpet please contact your flooring supplier.
Ensure that the sensor is installed well clear (min. 50 cm) of central heating pipes, water pipes, drains and electrical wiring. The sensor must be installed in the middle of a cable loop for optimal temperature registration. Ensure that the heating cables do not make direct contact with the conduit in which the floor sensor is mounted.
Before installing the Comfort Cable, the resistance reading should be taken and noted down on the inspection card in the center of this manual. The reading should be taken during the installation and on final completion. These readings should be as per the technical information (Point 2). Take measurements both between the resistance wires and between the resistance wire and the earth cladding. Keep this inspection card in the meter cupboard in a visible place! This forms part of your guarantee.
150+ Watts/m² for prime heating of normal rooms cable spacing 100 mm 100/125 Watt sq. m for comfort heating of normal rooms cable spacing 125/150 mm Example: for a conservatory of 20 sq. m floor surface multiply the total floor surface with the above mentioned capacities (20 x 150 Watt = 3000 Watt) Choose set 3300 - 3300 watt. Cable can be sized (or checked) by measuring the linear length i.e. Heat required 150 watts/m². Room size 4mx3m =12m² Cable spacing = 100mm Therefore 4mx30 = 120 linear mts. Use 2100 Watt set (124 linear mts). If there is any excess cable left after installation, you can space a few runs at 50mm at the window & door areas of the room to lose it in the floor. NEVER SHORTERN THE CABLE
Fit the cable end (marked with *******) through the electrical pipe to the back box for the thermostat. The word "splice" must stay visible. Splice must be covered by screed. Fix the spacer strips at 500 - 600 mm centres with masonary or Hilti nails. Attach the cable in a zigzag fashion with a distance between the cable as required. If reinforcing is used (Smooth Weld mesh at 100mm square) plastic tie wraps can be used for attaching the cable directly to the reinforcing. Extend the 2nd electrical pipe to about 50 cm from the wall and have it end in the middle of a cable loop. Pull the sensor cable to the back box and ensure that the sensor is in the conduit. Ensure the cap is placed on the end of the conduit so that replacing the sensor is always possible. Please contact your local Technical Department www.magnumheating.com if you require assistance on the spacing of the cable.
Typical questions asked about products:
How long is the delivery?
Is the product easy to fit?
Which options should I choose?